Stoneridge Terrace Campground Email Shady primitive area with new shower house. Dump station, flush toilets, showers, playground, basketball court, amphitheater, Olympic size heated swimming pool, Nestled in southern Medina County. Where peace and quiet is at its best. We can accommodate from the smallest tent Showers, flush toilets, dump station, tennis and basketball courts, playgrounds, large sandboxes, horseshoe pits, row and paddle boat Open to Open May 1st to 3rd weekend in October. Dump stations, sewer connection and city water, flush toilets, showers, laundromat
Huge difference between 30-amp and 50-amp hookups
Hooking up a amp vehicle to a amp power pedestal whenever possible will help protect the long-term dependability of appliances in your rig, Finch says. The breakers for the electrical systems in most campgrounds are designed with a tolerance of percent, plus or minus. If breakers tripped at exactly 30 amps, they would cost much more — perhaps 10 times as much — as breakers normally used. A amp outlet supplies 3, watts 30 amps multiplied by volts. Therefore, the breaker on that outlet could meet code and still trip anywhere between a total load of 2, watts 80 percent of 3, watts and 4, watts percent of 3, watts.
That sets up a situation where the breaker on a amp outlet may not trip until the load exceeds 4, watts.
I assume the RV has a 50 amp cord (NEMA L) on it that you are plugging into the 50amp to 30amp adapter (). The 30amp adapter has a L plug on it. A L plug will have V across the hots, as will your L plug on the RV.
The real first question you need to answer is whether your pop up is wired for 20 amps. Go find the electrical cord that is attached to your trailer’s breaker panel where it exits the body of the trailer. Take a close look at the male end of that cord. If it looks like a conventional household plug 2 vertical prongs and a ground spike , then your trailer is equipped for a 15 amp service.
If it has one vertical prong, a horizontal prong and a ground spike, then it’s a 20 amp fitting. If it has 2 prongs set a 45 degree angle with a ground spike underneath, then it’s a 30 amp fitting. Once you figured out what your trailer is equipped for, you can move on the step of obtaining the right adapters. If your trailer is equipped with a 30 amp plug, you won’t need an adapter, but you may need an extension cord to reach the power connection at your camp.
Avoid the temptation to use a household cord and a couple of adapters. Overloading a 15 amp cord can be dangerous and result in fires. Buy a proper 30 amp extension cord if necessary. If your trailer is equipped for either 15 or 20 amps, you’ll need an adapter to plug into the camp supply. As far as pre-cooling your fridge, I guess some folks would choose to do this because RV fridges use a holding plate design which takes longer to cool than does a household fridge.
Easy Generator to Home Hook Up
Description The shoreline cord is what gets connected to your RV bringing in power to your distribution center. Older models have a J Box, which has a receptacle coming from the generator and another that goes to the distribution center. This requires you to have to go outside and plug in the generator every time you want to use it. Newer models come with an automatic RV transfer switch already installed, eliminating the need to have to manually unplug from shore power and plug in the generator.
Jun 06, · I told him from reading on RV Net, etc. that I wanted a 10 gauge wire, 30 amp, volt dedicated circuit run to the outside of my garage so that my camper will have shore power. The electrician obviously messed up the volt part.
The first part, the 30 amp side of the socket, goes to the normal, everyday things we all use. It includes one of two air conditioners. The other side of the socket goes to the second air conditioner. Now let’s get the concept and not get hung up on “code”. A “code” 50 amp outlet is one that will provide for you 50 amps of volt AC. That outlet can also provide two separate 50 amp volt feeds. If your driving a coach with electric cooktops people in the newsgroups say they exist, apparently!
The normal motorhome doesn’t. It runs all but the back air from one side and it runs the rear air on the other. Based on this, if you were to put in a plug for your motorhome, you might want to consider that a more conservative, safer approach might be of benefit. You might be better served with a 30 amp and 20 amp breaker at the supply if you were going to draw but 30 and 20 amps. Unless you need a lot of power in some other application; unless you’re doing commercial welding or some such, the installation of a code outlet is a big waste of money and can be much more dangerous to you and your coach.
What I Wanted Most campgrounds I go to have a box that contains a 30 amp plug and a 20 amp plug. Most boxes like that are run from a 30 amp breaker on a main panel.
? for tent campers using electrical hookup
Our out of town service and repair clients will find it convenient in the event they arrive early for their scheduled service or repair appointment. The driveways through the resort are asphalt and each site is tastefully landscaped on each side. Additional facilities include an excellent laundry that features brand new commercial washers and dryers.
Our restroom and shower facilities have ceramic tile throughout, we get comments frequently regarding their cleanliness and are rated 10 by Good Sam. While our location is urban, as you enter the property you quickly feel the transition to a more peaceful and quiet park like setting. The reason for our name, Maple Grove, is based on the beautiful groves of Armstrong Maples that grace each site throughout the resort.
Jun 06, · Your circuit should begin with a 1 pole 30 amp breaker. Black on the circuit breaker. If your circuit breaker is where your meter is, the green and white wires go on the same grounding buss, assuming it has spare screws to tie them in.
RVs built for North America all use volt appliances, except for specialty heating products such as the Cheap Heat. That being said we have sold quite a few of the CheapHeat systems in the Europe because the CheapHeat system will work there with no modifications. Mike Sokol December 3, at My articles are read in at least 60 different countries, many of which have single-pole volt AC power at 50 Hz the UK for instance. Larry McGaugh December 3, at This happens sixty times a second.
This means that when Leg-1 of the VAC is going from 0 to volts positive. Leg two of the VAC is going from 0 to volts negative. Power is now taken from the two opposing hot legs and since they are degrees out of phase, the end result is VAC. When Leg-1 electrons are moving towards Positive volts the Leg-2 electrons are moving towards Negative Volts. In that scenario you have both Leg 1 and 2 electrons moving towards volts positive and then negative at the same time.
End result is an overloaded wire that will overheat and very possibly cause a fire. There are two simple ways, one is to install a surge protector that identifies incorrect phasing and locks out the power to the RV.
Easy Generator to Home Hook Up
All photos are thumbnails, click to see an enlarged version Power to your camper will be provided via a power distribution box located at your campsite. In this photo we see two breakers in the upper left, one 30 amp which controls the round “RV Style” socket below the breakers, and a 20 amp breaker which controls the “duplex” receptacle to the right. Remember this is what feeds the electric to most popups so verify that you pop up has working GFIs on all electric circuits.
In this photo we see three breakers in the upper left, one 30 amp which controls the round 30a “RV Style” socket below the breakers, one 20 amp breaker which controls the “duplex” v receptacle to the right as well as a 50a dual pole breaker for the 50a RV socket. Here you see the cord exiting the Pop-Up as well as the cord end. But, what do you do when the campsite only has a 20a receptacle.
Jun 07, · It is very important to know that in the RV world, 50 Amp service is Volts at 50 Amps from the NEMA receptacle that you can plug an MC into. On the other hand 30 Amp service is Volts at 30 Amps from a TT receptacle.
First why are you wanting to meter each individual campsite? It is usually way to expensive as you have found out. Don’t know how your campground is laid out, but if it is tight you could put a post on the inside corner of 4 sites. But you have to make sure that the way they would normally park their cord can reach the pole. The other big thing is to make sure you have large enough wire for the runs to insure that there is not a huge voltage drop to each site.
And to provide power for 2 air conditioners washer dryer plus plus I would need to add metered sites and prefab poles with meters cost a min of plus per unit. Plus the campground is in a area that do not see many big rigs. By this are you talking about these appliances in the RV?
Power Grip Max 50a Adapter – 55-7031
Tip by E ScottD on Step 14 3 days ago Upvote 0 A couple of things,that I can see that would help your project would be to install a ground rod on the generator or the box leading to the generator grounding the circuit. It could preclude instances of getting shocked if touching something energized a hotplate and a device already installed in the home the stove, range hood etc.. Adding a ground rod would help. Also don’t run any high end appliances while on generator unless you keep a close eye on the fuel level.
When the generator runs out of fuel, it dosen’t just stop, it runs down. While it is doing this it will decrease the amount of voltage to the house.
Like all true RV’ers, when we pull into our campsite we hope to have the luxuries that come from having full hook-ups including water, sewer and 30 or 50 amp .
Would you like to merge this question into it? MERGE already exists as an alternate of this question. Would you like to make it the primary and merge this question into it? MERGE exists and is an alternate of. However in an emergency you can live with a 5. You will not however be able to run an electric oven at all. To run an electric water heater almost everything else will have to be shut off. You will have to ration the power.
I am sure it is not the same as original. Will it damage my RV?
Camper Extension/Power Cords
Summary Do not assume you can put two rated cables together to extend your length. Length and wire size are tied together to give you minimal line loss. Two smaller wire sizes although rated at a specific amperage will not be big enough and you can see significant voltage loss. You do have the option to build your own cables. The important aspect is to use rated connectors and then match a length of wire that has appropriate wire size to minimize voltage losses.
The following information provides you with general information and links to specific cables that will provide you with what you need to get your appliances and tools connected.
When you wire up a R V 50 amp outlet, you will measure volts from hot to hot, volts from each hot to neutral, volts from each hot to ground, and finally zero (0) .
Is there anything I need to do besides buying an adapter from 30 to 50 amp plug in? Thanks for your input. Heartland Mallard M32 danemayer , Even though most campground pedestals will also have a 30 amp receptacle, it’ll be handy to have when you run into a pedestal that only has a Couldn’t that fry something in the trailer? After thinking about it, the 50 amp only allows the camper more room before it trips the breaker.
Electrical Question – 30 amp / single pole for RV
Alaska’s Camping Guide is going through an exhaustive update to insure the information on this site is accurate and correct for the coming camping season. Please contact us if any discrepancies, errors or omissions are noted. Campgrounds with Hook-Ups is just one portion of this all new comprehensive site. Like all true RV’ers, when we pull into our campsite we hope to have the luxuries that come from having full hook-ups including water, sewer and 30 or 50 amp electric to power the coach and its many accessories.
Having 50 amp service as your only option is an extremely rare occurrence so the average RVer does not need to carry a 50 to 30 amp adapter. Adapters For 50 Amp RVs 50 amp RVs are becoming more and more popular as more people want the freedom to run their .
Index Home About Blog From: John De Armond Subject: Mon, 03 Jan Used one for years with my catering trailers. It allows supplying a total of amps of volt loads. No worry about overloading the cordage laying out on the ground. The rating is conservative for when the cord is enclosed. Laying out on the ground I’ve found that I can crank at least 80 amps through a 10 gauge type SO cord before it gets warm enough to make me uncomfortable. I carry amp breakers including a amp volt breaker made by cutting a volt breaker apart in my “concession survival kit” that I can install and pull near amps of volt power.
On your RV, internal breakers will still limit the max amps to 30 amps or whatever. One tip – use “industrial” rated convenience outlets. The plastic is of much higher quality and the contacts are much heavier.
Can I Plug My 30 Amp RV Into A 50 Amp Plug Without Damage?
A Creative Solution RVers need to carry an assortment of electrical adapters to accommodate the various RV park power pole offerings. Many RVs today are wired for 50 amp service two 50 amp volt for a possible amps. Most RV parks offer 50 amp service either as standard or as an extra cost option. Smaller or older RVs may have only a 30 amp service one 30 amp volts. Most RV park power poles that offer 50 amp service also have a 30 amp outlet.
Older RV parks may only have the 30 amp outlet available.
And if your RV service panel is protected with a 30 amp main breaker, you are good to go. But if you do not have 30 amp protection on a 30 amp plug, and you begin to draw above 30 amps, you.
I just wouldn’t want to overwhelm a new person. The resources of Plugshare is good to show all charging resources that people have mapped out. But some RV parks just haven’t been tried or added to Plugshare yet. Camping sites like RVParky. Check for the ones that list “50 Amp” service, or call and ask them about it.
That is the outlet that comes with your Tesla charging cable. That should be all you need. But for a newcomer with zero experience this must be totally overwhelming: As essential as Plugshare is, it’s doesn’t have much for this category Use the apps from the sites Rocky suggested, or just KOA on the web. Since we had also rented a cabin to spend the night in, they didn’t charge us to use the RV slip outside of the cabin.